Slave E-Panel for a Dual Schneider Electric XW Plus inverter/charger system, Requires a Dual Master E-Panel. The XW inverter is mounted directly above the E-Panel for a 16 in wide assembly.
Inverter battery breaker
2 separate 60 amp AC inputs for generator and utility
Knockouts for up to seven din rail mount DC, DCGFP63 or AC breakers and 12 panel mount or DC-GFP80 breakers
Massive tin plated copper bus bars directly connect to the Schneider Electric XW’s battery terminals
Bus bars for AC inputs, AC output, neutral, ground, PV + in, PV- in, Bat +, Bat-
500 amp shunt (MNSHUNT)
Metal dead front behind the reversible door
Charge controllers mount to either side or both sides at once for dual controllers. (Note: The XW 60 amp controller can mount on the Right side only due to their isolated communications compartment)
AC bypass can be configured as input & output on/off as well as AC bypass.
The XW MPPT controller requires no mounting bracket. FM60, FM80 and Classic require Right or Left E-Panel charge control mounting brackets. Right hand bracket furnished standard.
Main Breaker Current Rating – 250 or 175
Number of spaces – 19
Environmental Rating – Type 1 (Indoor)
Max. Wire Size – 4/0
Max. AC Voltage – 240VAC
Max. DC Voltage – 300VDC
Warranty – 5 yrs.
Listed by ETL for US & Canada
Made in the USA