The MNPV6 Disco is very flexible. It is ETL listed for AC and DC. This allows you to configure it for several different uses. It will work with 1-6 150 volt DC breakers. The combiner also works with 1 600 volt DC breaker for a grid tie disconnect. You can also install a 240 volt AC breaker with the 600 volt DC breaker to make a complete disconnect for a grid tie inverter. Load Break rated. This configuration makes a compact Grid Tie disconnect for those applications where the built in switch won’t do the trick.
Convenient disconnect handle
All aluminum powder coated housing that won’t rust
Flip up cover that can stay in the open position during installation
PV Negative bus bar with 14 useable openings (10 #14-6 and 4#1/0-14)
Chassis ground bus bar with 14 useable openings (10 #14-6 and 4#1/0-14)
Standard din rail to mount up to 6, 150V or 3, 300 Volt breakers
120 Amp tin plated copper bus bar to combine breaker outputs – bus bar may be split in two
Dead front cover snaps into place after wiring is complete for safety
Knockouts for PV in and PV out on bottom and sides
Top surface is available to bring conduit in from directly above the enclosure
Enclosure only- NOT COMPATIBLE WITH THE BIRDHOUSE.